Development Services - Property Files
100TH AVE W
7/13/2017 2:16:27 PM
9/23/2020 4:08:10 AM
Legacy PermitTrax Document
PermitTrax File Description
Building Comments 2
House / Building Number
100TH AVE W
23200 100TH AVE W
Citizen's Connect Viewable
PermitTrax User ID
There are no annotations on this page.
Document management portal powered by Laserfiche WebLink 9 © 1998-2015
All rights reserved.
Page 1 of 1
Pages to print
Enter page numbers and/or page ranges separated by commas. For example, 1,3,5-12.
After downloading, print the document using a PDF reader (e.g. Adobe Reader).
Download electronic document
View plain text
<br />City of Edmonds <br />PLAN REVIEW COMMENTS <br />BUILDING DIVISION <br />(425) 771-0220 <br /> <br /> <br />DATE: May 13, 2007 <br /> <br />TO: Edmonds School District, Attention Matt <br /> FAX: 206-441-0478 <br /> <br />FROM: Ann Bullis, Assistant Building Official <br /> <br />RE: Plan Check #2007-0366 & 2007-0365 <br /> Project: Remodel Buildings F & H <br />th <br /> Project Address: 23200 100 Ave W <br /> <br />During re-review of the plans for the above noted project, it was found that the following information, <br />clarifications or changes are needed. Provide written responses to each comment and where changes can be <br />found on the plans. Please submit revised plans/documents to Theresa Umbaugh, Permit Coordinator. <br /> <br />1.Previous item 1: Note the Type of Construction on the coversheet of the plans. <br />2.Previous item 3 (for reference, room numbering was changed on the resubmitted plans): <br />a.The distance between required exit doors at Library H23 must be measured in a straight line <br />from door jamb to door jamb (IBC 1014.2.1). Sheet G002 shows the measurement of actual <br />travel distance which is incorrect. It appears it will not meet the minimum required <br />dimension. A new second exit door must be provided. <br />b.See item 3 below regarding staff lounge area (H13) <br />c.The occupant load modifications for classrooms are subject to approval by the Building <br />Official with the proposed Alternate Design. <br />3.Previous item 5: We disagree with the occupant load factor of 100 used for the staff lounge. The <br />appropriate factor would be 15 as was previously on the plans. 2 exits are required, unless you plan to <br />justify in your alternate design for occupant load modifications. <br />4.Previous item 7: The occupant load modifications for classrooms are subject to approval by the <br />Building Official with the proposed Alternate Design. <br />5.Previous item 8: Detail and hardware information for the proposed egress gates must be provided for <br />review at this time since it is a life-safety item. <br />6.Previous item 9: This item is still outstanding. It is the responsibility of the Architect of Record to <br />show all existing and proposed fire and life-safety information on the plans. As stated previously, these <br />building were built while under County jurisdiction and the City has no plans. The City cannot do a <br />complete review of the proposed project without this information. <br />7.Previous item 10: Still outstanding see item 6 above. <br />8.Previous item 14: See Building Official letter dated 5/10/07 <br />9.Previous item 15: See Building Official letter dated 5/10/07 <br />10.Previous item 20: On the coversheet list the exterior fences/exit gates as a separate permit. <br />11.The Alternate Design request submitted must specifically state which rooms the occupant load <br />modification is being requested for. Use room numbers and <br /> uses of space. <br />12.Clearly show on Sheet G002 which rooms/occupant loads are part of the request for Alternate Design <br />for the occupant load modification. <br />13.Alternate Design request must be stamped/signed by Architect of Record, Gerald Reifert. <br />
The URL can be used to link to this page
Your browser does not support the video tag.